Need To Know
ENTEC are a leading specialist contractor who supply and fit a wide range of automatic door operators, complete entrance packages and shop fronts into the retail, health, commercial, local authority and industrial market sectors.
You will find the following detailed on this page. Please click on the subject to take you to the relevant section:
- FIRE ALARM INTERFACE METHODS
- DOOR ENTRY AND ACCESS CONTROL SYSTEM INTERFACE METHOD
- RAL COLOUR CHART
- The Equality Act 2010 – The Equality Act 2010.docx
- Centre for Accessible Environments – www.cae.org.uk
- Disability Rights Commission – www.dredf.org
Please click on the link to see a configuration Fire Alarm Interface Detail
The attached detail above indicates the preferred method to interface an automatic sliding door with a fire alarm system.
This method simulates loss of mains voltage supply to the operator. The sliding doors are then taken to the open position under battery power contained within the operator. The battery power supply is constantly monitored to ensure it is always fully charged, this is a requirement with BS 7036 (96) and BS EN 16005. The doors will then remain in the open position until the mains voltage supply is reinstated, usually after re-setting of the fire alarm system, the operator will then self-reset and after one system check function will return into normal service.
Please note: The same method can be adopted for automatic swing doors which need to close upon activation of the fire alarm system, for instance where the door set may have a fire rating and need to be closed for containment purposes.
All the above would be supplied and installed by others.
An alternative method for fire alarm interface is as follows:-
To open either automatic sliding or swing doors please provide ONE NUMBER PAIR OF NORMALLY OPEN PAIR OF VOLT FREE RELAY CONTACTS WHICH CLOSE UPON ACTIVATION OF THE FIRE ALARM SYSTEM. This is usually provided via an “in the field” relay interface unit. Relay connections are to be terminated adjacent to our operator ready for final connection by our engineer. NOTE: This interface signal should be monitored as it is a normally open connection.
All the above apart from final connection of the interface signal is to be provided by others.
To interface automatic doors with a door entry or access control system will require an interface signal.
This interface signal needs to be as follows: -ONE NUMBER PAIR OF NORMALLY OPEN PAIR OF VOLT FREE RELAY CONTACTS WHICH CLOSES UPON AN AUTHORISED SIGNAL BEING RECEIVED FROM THE DOOR CONTROL SYSTEM.
This signal should be terminated adjacent to our operator ready for connection by our engineer.
Note: In some instances, especially where forced door indication is utilised, the door opening devices should all be provided by the door control system provider with the command to open signal being the only interface with the automatic door equipment.
Please do hesitate to contact us for further information regarding this interface method and the best and safest way to achieve a complaint entrance.
Please click on link to see RAL Colour Chart
Note: This is just an indication of the colour and not exact final result as different ways of viewing can distort.